Research on the protection coordination of permanent magnet synchronous generator based wind farms with low voltage ride through capability
© The Author(s) 2017
Received: 14 December 2016
Accepted: 9 May 2017
Published: 24 July 2017
To coordinate the protection of PMSG (permanent magnet synchronous generator), collector circuits and outgoing lines, a comprehensive and improved protection method of PMSG based wind farms with LVRT (low voltage ride through) capability is proposed. The proposed method includes adding a short time delay to the collector network current protection zone I and a directional protective relaying to the collector network protection, installing grounding transformers and zero sequence current protection, and generator low-voltage protection action improvement. A LVRT scheme consisting of variable resistance dumping circuit, grid side dynamic reactive power control and reactive power compensation control is proposed. The fault characteristics of PMSG based wind farms are analyzed, and a PMSG based wind farm in Dabancheng, Xinjiang, is used as an example to analyze typical wind farm protection configuration, the setting values considering LVRT requirements, and the coordination problems. Finally, an improved wind farm protection coordination methodology is proposed and its validity is verified by simulation.
As a clean and renewable energy, wind power is developing rapidly in China. In 2015, the new wind power installed capacity has reached 30,753 MW, an increase of 32.6% compared to 2014, and the total installed capacity has reached 145,362 MW, ranked first in the world.
Because of wind power’s stochastic and variable operation nature, the stable operation of grid integrated with large scale of wind power and the protection configuration of wind farms are facing enormous challenges. Therefore, for maintaining the stability and safe operation of the power systems, wind turbines require to have the low voltage ride through capability [1–5]. Nevertheless, in the event of grid side fault or voltage dip, wind farms often simply trip to protect the wind turbines [6, 7]. To solve the problem, many advanced LVRT technologies have been adopted by wind turbine manufacturers based on GB19963(2011), including reducing input power of the wind turbine side converter by controlling the pitch angle or limiting wind turbine electric-magnetic power , eliminating the unbalanced power on the DC bus by installing power dumping circuit or energy storage devices , and enhancing grid-side converter output power by using var compensation devices, adding auxiliary converter, or adopting reactive power control strategy . Though those measures can improve the LVRT capacity the wind turbine and wind farm fault characteristics can be changed , which potentially lead to misoperation and malfunction of their protection [12–14].
PMSG is an important type of wind power generator in China , and its market share has significantly increased in the last few years. For the protection coordination of PMSG, collector circuits and outgoing lines, this paper proposes a comprehensive and improved protection method of PMSG based wind farms with LVRT capability. The impact of various LVRT techniques on wind farm fault characteristics is considered. The rest of the paper is organized as follows. Section 2 analyzes and summarizes wind farm fault features and the research status on protection configuration. Section 3 proposes the LVRT scheme consisting of variable resistance dumping circuit, grid side dynamic reactive power control and reactive power compensation control, and analyzes the PMSG wind farm fault characteristics. In Section 4, a PMSG based wind farm in Dabancheng, Xinjiang, China is used as an example to analyze the typical wind farm protection configuration, its setting values considering LVRT requirements and its existing issues on the coordination among its protections. In Section 5, an improved wind farm protection coordination methodology is proposed and its validity is verified by simulation. Finally, conclusion and perspectives for future work are given in Section 6.
2 Research status of wind farm protection
2.1 Research status of wind farm fault characteristics
Existing researches have mainly focused on the criterion of fault current with little emphasis on fault characteristics of wind turbines (especially PMSG) with LVRT capability. Short circuit currents of different types of wind turbines show significant differences due to the different control strategies in [16–19], which can have a great impact on the protection setting. According to the flux balance equations and frequency-domain analysis, mathematical expressions of the short circuit current for doubly-fed induct generator (DFIG) are derived without considering the effect of the crowbar [20, 21]. However, the short circuit current characteristics will be different when crowbar circuit is used in DFIG wind turbines [22, 23]. The PMSG short circuit current does not normally exceed the rated current of the grid side converter . Control process of the full power converter that quickly isolates PMSG faults is analyzed in , and the short circuit current flowing into the grid is shown to be controllable. Therefore, the control strategy of LVRT of PMSG can affect the short circuit current characteristics, and the protection setting and configuration.
2.2 Research status of wind farm protection configuration
At present, most of the researches focus on the protection of the collector networks and outgoing lines of wind farms with little on protection and coordination of wind farms with LVRT capability. It has shown that wind farm integration and its fault current attenuation characteristics may reduce the reliability of current protection in power grids [26, 27]. Thus, the setting of wind farm collector network instantaneous protection should not only consider its short circuit current characteristics, but also require installing directional element if necessary [28, 29]. An adaptive protection method based on short circuit current characteristics is presented in [30, 31], which counters for different wind power output, short circuit current level and wind farm types. However, the presented researches have little consideration on LVRT control strategy for wind farm protection configuration and coordination.
3 PMSG wind farm fault ride through feature based on LVRT control strategy
3.1 LVRT methodology applied in PMSG
At present, there are three LVRT control methods used in PMSG, including reducing the generator side converter input power, eliminating the unbalanced power at the DC bus, and increasing the output power of the grid side converter. Although these methods can enhance wind farm LVRT capability, they all have noticeable shortcomings. For example, pitch angle control has slow response time and limiting the electromagnetic power of wind turbines leads to slow system recovery, discharging circuits have difficulty in heat dissipation and occupy large volumes, energy storage devices have high cost and complex control, reactive power compensation has slow response and limited capacity, and auxiliary circuits require large volumes and have high cost.
3.2 An improved and comprehensive LVRT control strategy
where U dcmax is the maximum DC bus voltage of the converter, and ΔP min is the power difference between the generator and grid side when the dumping circuit is initiated to operate.
The reactive power compensation device is formed of thyristor switched capacitors (TSC) in parallel with thyristor controlled reactors (TCR). The numbers of TSC and TCR installed can be modified according to the required reactive power compensation at certain voltage dip value and requirement to ensure grid voltage stability.
3.3 Fault ride through characteristics of wind turbines with LVRT capability
4 Protection configuration and coordination analysis of PMSG based wind farm
4.1 Wind farm typical protection configuration and its coordination analysis
4.2 Wind turbine protection configurations based on the LVRT requirement
Comparison between the conventional protection and improved protection
Voltage violation protection
Upper limit protection
Lower limit protection
Upper limit protection
Lower limit protection
Over current protection
Phase to phase fault
Voltage unbalance protection
Current unbalance protection
4.3 Protection and coordination analysis of power collection line
Three-section current protection setting of the collector network
The simulation results show that, when the fault occurred at K1, it is designed to be cut off simultaneously by the breaker at the low voltage side of G6’s transformer and the fuse at its high voltage side whereas the protection 1 is only considered as the backup protection of the fuse. However, as the fuse and protection 1 is not coordinated, a large numbers of wind turbines near G6 are falsely tripped off. At the same time, the current protection zone III of the non-faulted collectors may act and trip all the wind turbines, which is not in accordance to the stable operation of the wind farm. The problems caused by a three-phase fault at K3 and K5 are similar.
RMS current of the collector network when single-phase faults occurres at K1 ~ K6
Section I setting(A)
Studies show that the wind farm protection coordination functions well when three-phase fault occurres at K7, K8, and K9, which are all at the low voltage sides of the wind turbine transformers.
4.4 Protection and its coordination analysis of outgoing line
Setting values of outgoing line protection
Maximum and minimum voltages of the wind turbines connected to the collector network during a three-phase fault
Collecting power line
Maximum machine terminal voltage(p.u)
Minimum machine terminal voltage(p.u)
However, it needs to be noted that the generator minimum voltage is very close to 0.2p.u. If the fault location is near the PCC (point of common coupling), the voltage will be lower than 0.2p.u. and the generator protection may act and potentially lead to the trip of the whole wind farm, which is not in accordance to wind farm operation and successful reclosure of the outgoing line. It will be beneficial for the stability of wind power integrated grid when the generator can last 0.3 s to 0.6 s at very low voltage. Meanwhile, because of the wind farm capacity accounted for only a smaller proportion of the power system, the positive sequence and negative sequence impedances of the wind farm are far greater than that of the grid. For the unique wind farm grounding mode, its zero sequence impedance is far less than the impedances of its positive and negative sequence. When the wind farm outgoing line has a single phase-to-ground fault, zero sequence current will become the main component and consequently, the three-phase fault currents tend to become similar indicating obvious weak power characteristic (the results of two phase-to-ground faults are similar). This will seriously affect the accuracy of the phase selection element as whose criterion is current overshoot.
5 PMSG based wind farm protection coordination improvement scheme and its validation and analysis
5.1 Protection incoordination of PMSG wind farm with LVRT capability
Based on the researches in Section 4, there are 4 main issues with protection incoordination of PMSG based wind farms with LVRT capability: ① The current protection zone I for the collector network is in conflict with the fuse at the high voltage side of the turbine transformer; ② The reduced reliability of the non-fault collector’s current protection zone III; ③ The reduced reliability due to the incoordination between the collector current protection zone I and zone III; ④ The incoordination caused by wind farm’s operation characteristics.
5.2 Improvement for incoordination between collector current protection zone I and fuse at high voltage side of turbine transformer
The analysis shows that with the change of the fault location, the action time of the current protection zone I can be adjusted adaptively. To some extent, the LVRT capability can be improved when the fault location is closer to the bus. The smaller the protection time settings are, the quicker the fault can be removed. When the fuse is not reliable, as its back-up, the collector circuit protection with an inverse time-lag characteristic can remove the fault with a certain reliability and sensitivity.
5.3 Coordination improvement of on-fault collector circuits protection zone III
A directional protective relaying is added to the collector network protection. When the current flows towards the bus direction, its output is “0”, otherwise, it is “1”. In order to avoid maloperation, the non-fault collector protection has the capability of locking itself by judging the current direction regardless the fault location.
5.4 Coordination improvement between protection zone I and zone III of fault collector circuits
The protection incoordination discussed here mainly shows that the single phase-to-ground fault current of the collector network is less than the setting values of its current protection zone I, II and III. The main reason is due to the lack of zero sequence current path in the collector network. In order to overcome this problem, grounding transformer and zero sequence current protection should be installed.
In this case, the grounding transformer capacity is 450kVA and its neutral grounding resistance is 20 Ω. The zero sequence current protection setting values of the respective wind farm collectors are 14.1A, 12.9A and 11.5A, (reliability coefficient is 1.5). Furthermore, the action time should be 0.7 s, as same as the current protection zone III.
5.5 Modification of protection incoordination caused by wind farm operating characteristics
The simulation results show that when a three-phase fault occurs at the collector outlets (K2, K4, and K6 in Fig. 6), the generator terminal voltage always exceeds 0.05p.u and the turbines can stay connected for at least 0.1 s. These faults will be quickly isolated by the collector current protection whose action time is given in (3).
To tackle the existing coordination problem in PMSG based wind farms with LVRT capability, an improved wind farm protection coordination methodology is proposed. The proposed method adds a short time delay to the collector network current protection zone I to improve its coordination with the fuse at the high voltage side of the turbine transformer. Reliability improvement of the non-fault collector current protection zone III is achieved by introducing a directional protective relaying to the collector network protection, while reliability improvement of collector current protection zone I and zone III during single-phase faults are accomplished by installing grounding transformer and zero sequence current protection. Furthermore, improvement of low-voltage protection action is also achieved by modifying the generator protection action curve. Taking a PMSG based wind farm in Dabancheng, Xinjiang, China as an example, validity of the proposed method is verified.
Future work will investigate overvoltage problems caused by the turbine transformer winding breakdown, and the high voltage ride through method and protection incoordination modification potentially brought by this method.
All authors read and approved the final manuscript.
Open AccessThis article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.
- Zhou, W., Bi, D., Dai, Y., Cheng, L., & Xiong, S. (2017). Design of VSG testbed for LVRT of renewable energy [J]. Electric Power Automation Equipment, 37(1), 107–111.Google Scholar
- Zhang, Y., Zheng, T. Q., Ma, L., et al. (2013). LVRT of photovoltaic grid-connected inverter adopting dual-loop control [J]. Transactions of China Electrotechnical Society, 28(12), 136–141.Google Scholar
- Li, S., An, R., Xu, Z., et al. (2015). Coordinated LVRT of IG and PMSG in hybrid wind farm [J]. Electric Power Automation Equipment, 35(2), 21–27.Google Scholar
- Zhang, M., Li, N., & Wang, Z. (2014). LVRT ability of PMSG wind power system [J]. Electric Power Automation Equipment, 34(1), 128–134.Google Scholar
- Zhang, X., Hu, M., Wu, Z., et al. (2014). Coordinated LVRT control of wind power generation system based on VSCHVDC [J]. Electric Power Automation Equipment, 34(3), 138–143.Google Scholar
- Khatun MF and Sheikh MRI (2016) Low voltage ride through capability enhancement of DFIG-based wind turbine by a new topology of fault current limiter[C]//2016 2nd International Conference on Electrical, Computer & Telecommunication Engineering (ICECTE), Rajshahi: pp. 1-5.Google Scholar
- Carnielutti F, de Paris J, Massing JR, Pinheiro H, Tessele B (2016) A human-machine interface applied for a low-voltage-ride-through test system for grid-connected wind turbines[C]//2016 12th IEEE International Conference on Industry Applications (INDUSCON). Curitiba: pp. 1-8.Google Scholar
- Ananthababu, P., Trinadha, B., & Ramcharan, K. (2009). Performance of dynamic voltage restorer (DVR) against voltage sags and swells using space vector PWM technique[C]//International Conference on Advances in Computing Control and Telecommunication Technologies (pp. 206–210). Karnataka: IEEE.Google Scholar
- Abbey, C., & Joos, G. (2007). Super capacitor energy storage for wind energy applications [J]. IEEE Transactions on Industry Applications, 43(3), 769–776.View ArticleGoogle Scholar
- Morren J, Pierik JG (2004) Voltage dips ride-through control of direct-drive wind turbines[C]//39th Inter-national UPEC. Bristol: 934-938.Google Scholar
- Han, L., Li, F., Wang, C., Wang, H., & Weiwei, C. H. E. N. (2016). A survey on impact of wind farm integration on relay protection [J]. Power System Protection and Control, 44(16), 163–169.Google Scholar
- Zhang, B., Wang, J., Li, G., et al. (2012). Cooperation of relay protection for grid-connected wind power with low-voltage ride-through capability [J]. Electric Power Automation Equipment, 32(3), 1–6.Google Scholar
- Heming, L., Dong, S., Wang, Y., et al. (2013). Coordinated control of active and reactive power of PMSG-basedwind turbines for low voltage ride through [J]. Transactions of China Electrotechnical Society, 28(5), 73–81.Google Scholar
- Xiong, X., Zhang, H., & Ouyang, J. (2011). Simulation analysis on transient output characteristics of DFIG with SVC [J]. Power System Protection and Control, 39(19), 89–93. 99.Google Scholar
- Fan, X., Wang, W., Xie, Y., et al. (2016). Inverter Control Switching Between Grid-connected and Islanding Operating Modes of Permanent Magnet Wind Power Generation System in Low-voltage Microgrid [J]. Proceedings of the CSEE, 36(10), 2270–2783.Google Scholar
- Zhao, Z., Wu, W., & Wang, W. (2009). A Low Voltage Ride Through Technology for Direct-drive Wind Turbines Under Unbalanced Voltage Dips [J]. Automation of Electric Power Systems, 33(21), 87–91.Google Scholar
- Hu, S., Li, J., & Xu, H. (2007). Analysis on the Low- voltage-ride-through Capability of Direct-drive Permanent Magnetic Generator Wind Turbines [J]. Automation of Electric Power Systems, 31(17), 73–77.Google Scholar
- Yao, J., Liao, Y., & Zhuang, K. (2009). A Low Voltage Ride-through Control Strategy of Permanent Magnet Direct-driven Wind Turbine Under Grid Faults [J]. Automation of Electric Power Systems, 33(12), 91–96.Google Scholar
- Lin, H., & Chao, Q. (2010). Simulation study of modeling and control of direct drive wind turbine under grid fault [J]. Power System Protection and Control, 38(21), 189–195.Google Scholar
- Yihui, S. H. I., Zongxiang, L. U., & Yong, M. I. N. (2011). Practical Calculation Model of Three-phase Short-circuit Current for Doubly-fed Induction Generator [J]. Automation of Electric Power Systems, 35(8), 38–43.Google Scholar
- Vicatos, M. S., & Tegopoulos, J. A. (1991). Transient state analysis of a doubly-fed induction generator under three phase short circuit [J]. IEEE Transactions on Energy Conversion, 6(1), 62–68.View ArticleGoogle Scholar
- Guan, H., Zhao, H., & Liu, Y. (2008). Symmetrical short circuit analysis of wind turbine generator [J]. Electric Power Automation Equipment, 28(1), 61–64.Google Scholar
- Kawady, T., Feltes, C., Erlich, I., et al. (2010). Protection system behavior of DFIG based wind farms for grid-faults with practical considerations [C]//IEEE Power and Energy Society General Meeting (pp. 1–6).Google Scholar
- Morren, J., Pierik, J. T. G., & de Haan, S. W. H. (2004). Voltage dip ride-through of direct-drive wind turbines[C]//Proceedings of 39th International Universities Power Engineering Conference (pp. 934–938).Google Scholar
- Li, R., Gao, Q., & Liu, W. (2011). Characteristics of direct-driven permanent magnet synchronous wind power generator under symmetrical three-phase short-circuit fault [J]. Power System Technology, 35(10), 153–158.Google Scholar
- Yang, G., Li, X., & Zhou, Z. (2009). Impacts of Wind Farm on Relay Protection for Distribution Network and Its Countermeasures [J]. Power System Technology, 33(11), 87–91.Google Scholar
- Comech, M. P., Montanes, M. A., & Garcia, M. G. (2008). Overcurrent protection behavior before wind farm contribution[C]//The 14th IEEE Mediterranean Electro technical Conference, MELECON (pp. 762–767). Acacia: IEEE.Google Scholar
- Yuling Wen (2009) Study about Wind Power Short Circuit and Impact on Power System Protection[D]. Xinjiang UniversityGoogle Scholar
- Su, C., Li, F., & Wu, Y. (2011). An analysis on short-circuit characteristic of wind turbine driven doubly fed induction generator and its impact on relay setting [J]. Automation of Electric Power Systems, 35(6), 86–91.Google Scholar
- Jang, S. I., Choi, J. H., Kim, J. W., et al. (2003). An adaptive relaying for the protection of a wind farm interconnected with distribution networks[C]//Proceedings of the IEEE Power Engineering Society Transmission and Distribution Conference (pp. 296–302). Dallas: IEEE.Google Scholar
- Wen, Y., Chao, Q., & Tuerxun, Y. (2009). Study on adaptive protection of wind farm [J]. Power System Protection and Control, 37(5), 47–51.Google Scholar