- Original research
- Open Access

# A measurement-based approach for power system instability early warning

- Feifei Bai
^{1}, - Yong Liu
^{2}, - Yilu Liu
^{2, 3}, - Kai Sun
^{2}, - Navin Bhatt
^{4}, - Alberto Del Rosso
^{4}, - Evangelos Farantatos
^{4}and - Xiaoru Wang
^{1}Email author

**1**:4

https://doi.org/10.1186/s41601-016-0014-0

© The Author(s) 2016

**Received: **10 May 2016

**Accepted: **10 May 2016

**Published: **20 June 2016

## Abstract

Early warning of impending instability in a power system under disturbance conditions is important for preventing of system collapse. A measurement-based approach is proposed to assess the potential power system transient instability problem under cascading outages. Where a measurement-based index is obtained as the estimation accuracy of a linear autoregressive exogenous (ARX) model to estimate the dynamic response of the power system and indicate the system stability to some extent after a disturbance. The proposed approach was verified using a set of marginally stable cases in a 179-bus WECC equivalent power system. Then the instability early warning threshold for this system is obtained as 0.44.

## Keywords

- Autoregressive exogenous model
- Accuracy index
- Dynamic response estimation
- Instability early warning
- Measurement-based

## Introduction

With the interconnections of power system increasing, the instability assessment is becoming more and more important for safe operation of power systems. The power system stability refers to the continuance of intact operation following a disturbance, it depends on the operation and the nature of the physical disturbance [1, 2]. The 2003 blackout occurred in N.E. North America is partly because of the lack of supportive applications when the system is close to instability [3]. If power system is close to the stability limit, actions must be taken by system operators to identify critical states. Therefore, it is very important to have an index for the critical situation awareness. A series of disturbances can increasingly stress the system, degradation of its stability margin may finally lead to loss of stability. Therefore, the analysis of system dynamic response during or after the disturbance is very important to indicate the potential instability of the power system [4].

The conventional methods of power system analysis are based on numerical solution of system differential algebraic equations. These numerical methods need more detailed representation of the power system but they are not suited for online application of stability assessment and control. There are three reasons: 1) The power system dynamic model could not include all the details of the power system; 2) The topology of the power system changes all the time; 3) The long computation time of the numerical solution. With a large number of synchrophasors being deployed, it is possible to construct power system model based purely on real-time synchrophasor measurements, which also can make on-line power system instability awareness feasible. Studies have been done with the measurement data for the system instability assessment [5–11]. Some focus on using real-time phasor measurements with pre-existing knowledge obtained from computer simulation results or historical events to enable real-time assessment under disturbance conditions [8, 9]. Some use selected real-time measurement locations to directly compute energy functions for the potential of instability [10, 11]. An adaptive power system equivalent method for real-time estimation of stability margin using phase-plane trajectories was proposed in [7]. This paper proposes a new method for instability early warning only using continuous high-sampling-rate measurements. In order to create the system collapse case, the idea in [7] using a series of disturbances to stress the system was used in this paper. Then an index was proposed to assess the potential instability of the system.

The rest of the paper is organized as follows. Section II is the introduction of the measurement-based system dynamic response estimation model and the model accuracy index. Section III is to implement the proposed model accuracy index to evaluate the system instability. Section IV is the case study of the proposed method. Conclusion and future work are provided in Section V.

## Methodology of the proposed approach

### Dynamic response estimation

A concept of dynamic response estimation for power system was proposed in [12]. It is to estimate the dynamic response of the power system during or after disturbances. The basic idea of the dynamic response estimation is to identify the real-time dynamic model or the transfer function of the power system and use the obtained model to estimate the dynamic response of the power system.

### The ARX model structure

*t*is the time index, and

*e(t)*is a white noise,

*z*

^{−1}is a backward shift operator and

*z*

^{−1}

*y*(

*t*) =

*y*(

*t*-1).

*n*

_{ a },

*n*

_{ b },

*n*

_{ c },

*n*

_{ d },

*n*

_{ f }are the orders of the signal

*y*(

*t*),

*u*(

*t*), and

*e*(

*t*), respectively. If

*C*(

*q*) = 1,

*D*(

*q*) = 1 and

*F*(

*q*) = 1, then (1) becomes to be the AutoRegressive model with eXogenous inputs (ARX) model. The mathematical structure expression of the ARX model is also can be described by the equation:

*N*is the total data points,

*ŷ*(

*k*)and

*y*(

*k*)are the actual response and estimated response, respectively.

### Model accuracy index

where *Y*,*Ŷ*,\( \overline{Y} \) are the estimated response by the ARX model, measured response by PMU/FDR, and the mean value of the measured response, respectively. This index is the accuracy of the model estimation in describing system dynamic characteristics. A fitness of 100 means a perfect fit between the estimated response and the actual response, while a fitness of zero means the estimated response Y is no better than the mean value of measured response\( \overline{Y} \).

*F*is the fitness index defined in previous study and

*A*is the normalized accuracy index. The accuracy index of instability assessment threshold can be determined as:

*A*

_{max}is the maximum one among all the calculated accuracy index in marginally stable cases. T is the maximum value of the accuracy index of the last disturbance before instability. The accuracy represents the difference between the actual response at the output location and the response estimated by the ARX model.

## Method for instability awareness

### Capability of accuracy index for instability warning

The application of the linear ARX-structured modeling method is under the assumption that the power system to be modeled is relatively linear around certain operation points. Although the power system is nonlinearin nature, the operating point of the large-scale power grid does not change dramatically generally. The power system shows linear characteristics most of the time and thus ARX-structured method may have merit in bulk power grid modeling [24]. However, when a series of disturbances are increasingly stressing the system, the system will become less and less stable so that the trained ARX model will tend to be less accurate to estimate the dynamic response under the changed topology, which will be reflected as the accuracy index becoming lower. The threshold for the instability early warning was obtained when the system under the marginally stable situation after cascading outage. Marginally stable means the system is pushed to the edge of the stability, no matter how small a disturbance is added to this system, the system will collapse. The threshold is the estimation accuracy index of the marginally stable case.

### Guideline for instability early warning

While a series of disturbances are increasingly stressing the system, degradation of its stability margin may finally lead to the system collapse. Continuous measurements on the monitored variables at a high sampling rate enable the ARX dynamic model to estimate the dynamic response in real time, and the model accuracy index obtained from the ARX dynamic model can indicate the decreasing of the stability margin. Therefore, a precisely defined threshold for instability early warning is necessary. Incidents of instability on a power system are not many, but they generally are accompanied by severe consequences. Therefore, the off-line dynamic simulation is the most convenient way to derive the threshold of the model accuracy index.

- (1)
For a specific critical area, create

*N*marginally stable simulation cases using a sequence of line faults. - (2)
For each simulation case, find the interface of the critical area and choose the input and out channel in each side of the interface, respectively. Then develop an ARX model using a period of system response data following the first disturbance.

- (3)
After obtaining such a model, the system responses following the rest of the disturbance sequence are applied to the model to perform the response estimation.

- (4)
Accuracy index values are obtained after disturbances.

- (5)
Repeat Step (2), (3) and (4) for

*N*marginally stable cases. - (6)
The threshold could be determined as the largest accuracy index of the last disturbance before collapse in all the

*N*marginally stable cases. - (7)
Using the developed model to estimate the system response, if the accuracy index is equal or smaller than the threshold, a warning signal indicating potential instability following the next disturbance will be generated.

## Case study for system instability early warning

### Marginally stable case

Marginally stable means the system is pushed to the edge of the stability, no matter how small a disturbance is added to this system, the system will collapse [7].

Using the same approach as in [7] to create the marginally stable cases, a sequence of three-phase line faults is used in this case to drive the interface between area “0” and “1” to its marginally stable point. As an example, a marginally stable case is created by five faults occurring at different locations (C1, C2, C3, C4 and C5 in Fig. 2). The first four clearing time of line faults was fixed (five cycles), and the last one was adjusted to make this case to be marginally stable, which means the system would collapse if the clearing time of the last fault increase by 0.001 s. A lot a simulation cases were carried out using this method, only eight marginally instable cases can be created. Please note that each fault is cleared by opening the fault line. They increasingly weaken the interface but do not break the connection. This case can increasingly stress the operating condition (weakening the topology around that interface) by series of permanent faults.

### Threshold for instability early warning

A threshold is needed to alert the system operator in order to prevent the system being pushed to instability. The proposed threshold determination method is applied in this section by investigating the instability problem between areas “0” and other areas.

## Case study and results

As shown in Fig. 5, the system tends to be less and less stable as more line disconnection disturbances added into the system, which is accompanied by the accuracy index of the system dynamic response decreasing, which indicates that the model accuracy index can be used to indicate the system stability to some extent.

Most of the accuracy indices in all the cases decrease due to the sequences of disturbances in Fig. 6. The difference of the disturbance location may be the main factor for special case 4 and case 8 why did not keep decreasing all the time. For all the simulation cases, after the fifth disturbance, the system is pushed to be marginally stable and most of the accuracy index also reaches its lowest point at the same time. The threshold can be obtained by the majority situations. It should be noted that this is a preliminary investigation on threshold value determination for system transient instability early warning. More studies need to be done to obtain further insight into the relationship between accuracy indices and potential instability for future work. The study in this paper is only an example to show how to derive the threshold with the proposed method.

For step 6 of the method described above, the threshold for this particular application is suggested as 0.44, the largest accuracy index value before collapses, as shown in Fig. 6. It means when the accuracy index reached 0.44, the system is almost stressed to its marginally instable point. For other cases, events with accuracy indices less than 0.44 are not necessarily instable, however, severe enough to alert for potential instability. This particular threshold selection method here only gives a “safe zone” of system operation, which means that no emergency control action is necessary if the index is higher than this threshold.

## Conclusion

A measurement-based power system instability early warning index was proposed. The verification results prove that the proposed index can indicate the potential instability of the system. The preliminary results have shown that the instability threshold can be used to early warn the instability caused by cascading outages. Future work will focus on how to prove the effectiveness of the measurement-based instability early warning approach theoretically and more studies to explore the possibility of the application in the real power system.

## Declarations

### Acknowledgment

The authors gratefully acknowledge FNET/GridEye group and all the EPRI project team members.

This work was partial supported by Electric Power Research Institute and also made use of Engineering Research Center Shared Facilities supported by the DOE under NSF Award Number EEC1041877 and the CURENT Industry Partnership Program. DOE under NSF Award Number EEC1041877 and the CURENT Industry Partership Program.

**Open Access**This article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.

## Authors’ Affiliations

## References

- IEEE/CIGRE Joint Task Force on Stability Terms and Definitions. Definition and classification of power system stability[J]. IEEE Trans Power Syst. 2004;19(3):1387–401.View ArticleGoogle Scholar
- Blankenship GL, Fink LH. Statistical characterizations of power system stability and security. In: Proc. 2
^{nd}Lawrence Symp. Berkeley, CA: Systems and Decision Sciences; 1978. p. 62–70.Google Scholar - Andersson C. Power system security assessment:application of learning algorithms. Sweden: Lund University, Licentiate Thesis; 2005.Google Scholar
- Ewart DN. Whys and wherefores of power system blackouts. IEEE Spectrum. 1978;15:36-41.Google Scholar
- Kamwa I, Grondin R. PMU configuration for system dynamic performance measurement in large multi area power systems. IEEE Trans Power Syst. 2002;17:385–94.View ArticleGoogle Scholar
- Sun K, Luo X, Wong JM. Early warning of wide-area angular stability problems using synchrophasors. San Diego: IEEE PES Power and Energy Society General Meeting; 2012. p. 1–6.Google Scholar
- Sun K, Lee S, Zhang P. An adaptive power system equivalent for real time estimation of stability margin using phase-plane trajectories. IEEE Trans Power Syst. 2011;26:915–23.View ArticleGoogle Scholar
- Sun K et al. An online dynamic security assessment scheme using phasor measurements and decision trees. IEEE Trans Power Syst. 2007;22:1935–43.View ArticleGoogle Scholar
- Ma J et al. Use multi-dimensional ellipsoid to monitor dynamic behavior of power systems based on PMU measurement. In: Proc. IEEE PES General Meeting. 2008.Google Scholar
- Quintero J, Liu G, Venkatasubramanian V. An oscillation monitoring system for real-time detection of small signal instability in large electric power systems. In: Proc. IEEE PES General Meeting. 2007.Google Scholar
- Messina AR et al. Interpretation and visualization of wide-area PMU measurements using Hilbert analysis. IEEE Trans Power Syst. 2006;21:1763–71.View ArticleGoogle Scholar
- Liu Y, Sun K, Liu Y. Measurement-based power system dynamic model for response estimation. San Diego: IEEE PES General Meeting; 2012. p. 1–6.Google Scholar
- Eriksson R, So X, Der L. Wide-area measurement system-based subspace identification for obtaining linear models to centrally coordinate controllable devices. IEEE Trans Power Del. 2011;26(2):988–97.View ArticleGoogle Scholar
- Kamwa I, Gerin-lajoie L. State-space system identification-toward MIMO models for modal analysis and optimization of bulk power systems. IEEE Trans Power Syst. 2000;15(1):326–35.View ArticleGoogle Scholar
- Zhou N, Pierre J, Hauer JF. Initial results in power system identification from injected probing signals using a subspace method. IEEE Trans Power Syst. 2006;21(3):1296–302.View ArticleGoogle Scholar
- Ghasemi H, Canizares C, Moshref A. Oscillatory stability limit prediction using stochastic subspace identification. IEEE Trans Power Syst. 2006;21(2):736–45.View ArticleGoogle Scholar
- Sarmadi SAN, Venkatasubramanian V. Electromechanical mode estimation using recursive adaptive stochastic subspace identification. IEEE Trans Power Syst. 2014;29(1):349–58.View ArticleGoogle Scholar
- Chaudhuri NR, Domahidi A, Majumder R, Chaudhuri B, Korba P, Ray S, Uhlen K. Wide-area power oscillation damping control in Nordic equivalent system. IET Gener Transm Distrib. 2010;4(10):1139–50.View ArticleGoogle Scholar
- Bai F, Liu Y, Liu Y, et al. Measurement-based correlation approach for power system dynamic response estimation. IET Gener Transm Distrib. 2015;9(12):1474–84.View ArticleGoogle Scholar
- Yao W, Jiang L, Wen JY, Wu QH, Cheng SJ. Wide-area damping controller for power system interarea oscillations: a networked predictive control approach. IEEE Trans Control Syst Technol. 2015;23(1):27–36.View ArticleGoogle Scholar
- Bai F, Liu Y, Sun K, Bhatt N, Rosso AD, Farantatos E, Wang X. Input Signal Selection for Measurement-Based Power System ARX Dynamic Model Response Estimation. Chicago, IL, US: IEEE PES T&D Conference; 2014.View ArticleGoogle Scholar
- Kundur P. Power System Stability and Control. New York, NY, USA: McGraw-Hill; 1994.Google Scholar
- Ljung L. System identification: theory for the user. 2nd ed. New Jersey: PTR Prentice; 1999. p. 1–296.Google Scholar
- Liu Y, Sun K, Liu Y. A Measurement-based Power System Model for Dynamic Response Estimation and Instability Warning. Electr Power Syst Res. 2015;124:1–9.View ArticleGoogle Scholar
- Sun K, Hur K, Zhang P. A New Unified Scheme for Controlled Power System Separation Using Synchronized Phasor Measurements. IEEE Trans Power Systems. 2011;26(3):1544–1554.Google Scholar