- Case study
- Open Access
Optimal configuration analysis for a campus microgrid—a case study
© The Author(s) 2017
- Received: 28 April 2017
- Accepted: 6 June 2017
- Published: 24 June 2017
The foremost issues of 21st century are challenging demand of electrical energy and to control the emission of Green House Gases (GHG) emissions. Renewable energy resources based sustainable microgrid emerges as one of the best feasible solution for future energy demand while considering zero carbon emission, fossil fuel independency, and enhanced reliability. In this paper, optimization and implementation of institutional based sustainable microgrid are discussed based on cost analysis, carbon emission, and availability of energy resources. Various microgrid topologies are considered for addressing the most ideal solution. The metrological data such as irradiance is acquired from solar satellite data of NASA (National Aero Space Agency) while the data for wind speed is taken from synergy enviro engineer’s site. HOMER® simulation tool is used for modelling and optimization purpose.
- Distributed generation
- Renewable energy resources
- Battery bank
- Diesel generator
- Solar photovoltaic system
- Wind turbine system
Worldwide, the demand of energy is increasing day by day, if the conventional methods of bulk power generation are not changed then this will lead to major environmental concern because of high carbon emissions which ultimately affect the human health and ecological system badly. To avoid hazardous effect of global warming and due to environmental concerns, government and key stakeholders are now switching the way of power generation from conventional sources to sustainable and renewable energy resources .
People in developed countries, have access to reliable and high quality power supply but in developing countries like India, people from most of the states are facing various issues related to poor quality of power supply like frequent power outages, inadequate grid capacity and huge power losses from transmission and distribution network. These problems are very common almost in all rural areas of India . All these issues can be sorted by transforming to microgrids which will not only provide more efficient and reliable power but also provide opportunity to the people of developing countries to live a better life, free from hazardous and polluting emissions.
Future power supply will be less dependent on conventional method of power generation because fossil fuels are limited for energy production and public awareness for environment protection are also increases globally. So, there is a need of power generation from environmental friendly techniques. These technologies include power generation from photovoltaic, wind, geothermal, biomass etc. also known as renewable sources of power generation and power generation from non-conventional technologies such as microturbines and fuel cells. These types of power generation sources generally come in distributed generation system and may operate in standalone and grid connected mode depending on the requirement of the system. For example, in remote areas and in faulty conditions these power sources mostly operate in standalone mode otherwise in grid connected mode . Several desirable factors like easy siting, less environmental impact, enhanced system efficiency, security and reliability improvement, power quality enhancement and congestion management in transmission and distribution network due to peak shaving reduction can be achieved by employing these technologies . Major concern associated with the use of renewable energy resources is their intermittent nature depending on weather conditions due to which the integration and operation of a microgrid becomes a challengeable task. This issue can be sort out using microturbines, diesel generators, small gas turbines and with the help of high density energy storage devices . However, the use of energy storage devices may not be economical and their use mainly depends on location and other system configurations.
Microgrid can be defined as a part of distribution network including one or more distributed energy sources and having the capability to operate either in grid connected or standalone mode deployed in a limited geographical area . There are various available favourable sites for the implementation of microgrids like remote areas, rural areas etc. where plenty of renewable energy resources are available for clean and green power generation. In such locations, microgrids can be operated in an islanding mode to achieve reliable and stable power supply by combining loads with the distributed energy resources available on the respected site. Based on market segments, microgrids can be categorized into five types: i) remote “off-grid” Microgrids ii) Campus/Institutional microgrids iii) Military base microgrids iv) Community/Utility microgrids and v) Commercial and Industrial microgrids . Other way to categorize microgrid is based on the output voltage supplied to the load, and according to it microgrids can be classified into two types i) AC microgrid and ii) DC microgrid. There are many factors which makes microgrids very important, some of them are as follows: During the conditions of blackout, natural disaster etc. microgrids can maintain the normal power supply in the system, cost of Transmission and Distribution (T&D) losses will be saved with the help of microgrid, Demand of electricity is increasing day by day which ultimately require expenditure in T&D expansion, microgrids can defer these expenditures, microgrids generally uses renewable energy sources for power generation and these sources are environmental friendly having almost zero emission, quality and reliability of power supply is also enhanced with the help of microgrid in remote locations by means of renewable energy sources and combined heat and power (CHP) generation, cost of energy can be greatly reduced and so on .
In this paper, various topologies of microgrid are analysed to find out the best possible configuration in terms of achieving various desirable objectives like better economical configuration as well as reduction in global warming, co2 footprints and other environmental problems.
The paper is structured into seven sections; first section gives the introduction of the research work, while section 2 discusses the objectives of the research work, and section 3 gives the detailed description of considered test system along with its load profile. Section 4 discusses the cost analysis for a typical microgrid while section 5 elaborates the system components, resources and modelling in detail. Section 6 gives the discussion on the results obtained through simulation considering six different cases and section 7 concludes the findings of the paper.
To reduce the dependency on fossil fuels and conventional method of power generation.
To make a zero-carbon nature through maximum utilization of renewable energy resources with the help of microgrid.
Help government of India and other major stake holder in realizing faster adoption of microgrids for ecological and environmental benefits.
To reduce the purchases of energy from the grid.
To provide a reliable, sustainable, economical, innovative, and optimize power system in the form of microgrid for commercial and residential purposes.
The demand of energy is rising from various sectors of society such as industries, resident as well as educational Institutes. On national as well as international scale, there are vast list of universities with growing number of departments, canteens and hostels. They added up a mass amount of energy demand on utilities, which can be made independent over the conventional sources by deploying microgrid system using renewable and non-conventional sources of energy. The educational institutes have a responsibility to become a role model for the nation to save energy and promote optimization. They should also develop and promote indigenous technology. They support many faculties and training facilities which can be a good platform to raise the awareness and promote energy saving . For the case study Aligarh Muslim University (AMU) is taken, which is situated in western Uttar Pradesh, India. The study of electricity consumption trend in AMU provides vital information that can be used to analyse, design and implement a suitable solution for the deployment of microgrid that can cut down the electricity usage from conventional grid and GHG emissions, thus save environment.
3.1 Electricity Consumption
Approximate Daily Electric Load Consumption of Hostel
Water Cooler a
Uttar Pradesh Power Corporation Limited (UPPCL) sanctioned a load of 6.1 MVA to the campus of this university. But due to increase in load demand, university consumption overshoot the limit of 7.952 MVA in Nov 2014 followed by 7.880 MVA in August 2015 .
3.2 Load Profile
Several initiatives have taken by vice chancellor for green and clean campus. In this regard microgrids are investigated for residential halls. Nadeem Tarin hostel is one of them which is taken for case study, it includes 146 rooms as non-sensitive load while dining hall, reading room, Common room and provost office can be considered under the category of sensitive load.
The details of different types of load commonly used in this hostel are listed in Table 1.
It is to be noted that fixed cost for various Distributed Energy Resources (DERs) incurred due to primary equipment cost and installation does not depend upon power dispatch and can be treated as a constant. Also for DERs which requires a converter for AC/DC conversion the cost of converters is included in the fixed costs. The main aim of the cost function formulation is to consider the cost of dispatchable units, such as diesel generator, cost of non dispatchable units, e.g. PV, wind, battery storage and cost of power purchased or sold to grid. The operational cost of the microgrid is the sum of all cost incurred in the system . Also, hourly emission from each DER unit is considered to optimize the carbon footprints and levels of pollution from the operating microgrid.
4.1 Cost of diesel generator
Where, Pdg is the power generated by diesel generator in kW, Eff is the efficiency of diesel genset and Fdg is the fixed cost of diesel generator comprising of equipment and installation cost.
4.2 Cost of PV generator
Where, Ppv is the power generated by the PV generator in kW, Cmpv is the maintenance cost of PV panel and Fpv is the fixed cost.
4.3 Cost of Wind generator
Where Pw is the power generated by the PV generator in kW, Cmw is the maintenance cost for the wind generator and Nw is combined equipment and installation cost.
4.4 Cost of Battery Storage
Where P bs is the power charged into the battery system and C mbs is the maintenance cost for the battery and C b is the cost of the battery. It is to be noted when the BS supplies deficit energy to the microgrid then Pbs is negative denoting revenue for the battery owner.
4.5 Cost of grid supply
Where α is cost of electric unit supplied from the grid in INR/kWh.
In case when the excess energy is sold to the grid, the factor β is the selling rate of power in INR/kWh and P grid is negative in order to balance the cost equation and generate revenue for the microgrid. In a typical microgrid scenario, β > α, however the tariff structure varies from location to location.
U.S. National Renewable Energy Laboratory (NREL) developed HOMER® optimization tool for better designing and planning of microgrids which are mainly fuelled by renewable energy resources. After considering various design topologies and uncertain parameters like future fuel prices, wind speed, load growth etc., HOMER® finds out the best optimal results. HOMER® supports the integration of renewable energy resources with the utility grid and works effectively in the stand alone as well as grid connected mode of operation of microgrids . Using HOMER® optimization tool, one can check and analyse large number of optimal combinations of various types of i) power sources: wind turbine, solar photovoltaic (PV), microturbine, fuel cell, biomass, utility grid, diesel generator etc. ii) energy storage technologies: battery bank, flow batteries, hydrogen, fly wheels etc. and iii) loads: daily profile with seasonal variation, deferrable, thermal etc.
In HOMER® optimization tool, the total Net Present Cost (NPC) is taken as an economically preferable quantity that is used in an optimization process. This NPC includes all the system costs like grid cost, operation cost, replacement cost, maintenance cost, capital cost, fuel consumption cost and other types of miscellaneous cost. Based on the inputs provided by modeler like resource availability, technological options, equipment costs etc., HOMER® simulates different system configurations and as per NPC it displays all the possible techno-economic feasible configurations. The simulation results of HOMER® comes in the form of tables and graphs which ultimately helps modeler in comparing too many feasible configurations simultaneously and ranking them as per techno-economic basis.
Simulation, Optimization and Sensitivity Analysis are the three most important tasks performed by HOMER®. These three parameters evaluate techno-economic feasibility of various available technological options after accounting all possible variations in electric load, energy resource availability, technology cost, etc. i) Simulation: For an entire year and in time steps from 1 min to 1 h, HOMER® simulates the operation of a hybrid microgrid. In this area, HOMER® determines the technical feasibility and lifecycle cost of a hybrid microgrid. The optimization and sensitivity analysis tasks of HOMER® mainly depends on the capability of simulation task. ii) Optimization: In a single run, HOMER® inspects all the possibilities and as per optimization variable of choice, it sorts the system accordingly. In this area, based on search space defined by modeler, minimum total net present cost, constraints, etc., HOMER® displays all the feasible results and system configurations. iii) Sensitivity Analysis: In a single run HOMER® compares and checks thousands of possibilities. In this area, HOMER® checks the importance of all parameters variations and aspects with time by running and comparing the results of thousands of simulations. HOMER® finds out the optimal results based on different sizes and quantities of the equipment’s along with constraints as defined by user. If the modeler is not confirmed about the best value of any particular variable, then with the help of sensitivity analysis modeler can enter different possible values of that variable and sensitivity analysis shows how the simulation results depends on these values.
List of some important parameters
Max Power Current
Max Power Voltage
Wind Turbine (WT)
Hub heights available
37 m, 31 m, 25 m, 21 m
Rated rotor speed
Rated output voltage
400 VAC, 50 Hz
Working wind speed
Power Capacity (kW/kVA)
1kWh Lead Acid
Round Trip Efficiency
Maximum charge Rate
Maximum charge Current
Maximum Discharge Current
Initial State of Charge
Minimum state of Charge
310 V-450 V
-25 to 55O C without de-rating
In this paper, energy demand of the hostel is addresses with the help of different topologies. The daily average load of 992.43 kWh/d with peak load of 171.78 kW is considered for modelling in HOMER®. The details of different system components used in this paper are as follows.
5.1 Solar photovoltaic system
PV panel size, solar radiation and PV cell temperature are some factors which can affect the generation of electrical power supply from solar energy. Lifetime of 25 years are assumed for PV panel and the size of PV panel is varied from 140, 145, 150, 155, 160 kW to evaluate better results.
f PV : Derating factor of PV
Y PV : PV array rated capacity (kW)
I T : Global solar radiation incident on the surface of PV array (kW/m2)
I S : Standard amount of radiation used to rate the capacity of PV array (1 kW/m2)
Monthly average solar global horizontal irradiance data
Daily Radiation (kWh/m2/day)
5.2 Wind Turbine System
Wind speed and tower height are the main factors which can affect the electrical power supply from wind energy. Lifetime of 20 years are assumed for wind turbine and the size is varied from 90, 95, 100, 105, 110 kW to evaluate better results.
P r : Mean rated power
v ci : Cut-in wind speed
v co : Cut-out wind speed
v r : Rated wind speed
Monthly average wind speed data
5.3 Diesel Generator System
Since, renewable energy resources are intermittent in nature, so there are chances of complete and partial outages of these resources due to which diesel generator is required as a backup source for meeting the electrical demand of primary load.
Minimum load ratio and lifetime hours of diesel generator are taken as 25% of 15000 respectively for modelling.
C om,gen : Operation and maintenance cost (INR/hour)
C rep,gen : Replacement cost (INR)
R gen : Generator lifetime (hours)
F o : Fuel curve intercept coefficient (fuel/hour/kW)
Y gen : Generator capacity (kW)
C fuel,eff : Effective price of fuel (INR/quality of fuel). It includes the cost penalties associated with the emission of pollutants from the generator.
5.4 Battery Bank System
Battery bank size, battery charge and discharge rate are the main influencing factors associated with the power output of the battery bank system. Batteries are essential in hybrid power system to store surplus electrical energy generated through renewable energy resources during low demand periods and to release deficit energy during shortage and high demand periods respectively. Lifetime throughput of 800 kWh are assumed for battery bank and the size is varied from 240, 245, 250, 255 kWh to evaluate better results.
SOC(t) and SOC(t − 1): State of charge at time (t) and (t-1)
Q: hourly discharging rate
E: Total energy
e cd : Efficiency of charge and discharge
N batt : Number of batteries in a battery bank
Q lifetime : Lifetime throughput of a single battery
Q thrpt : Total amount of energy that cycles through the battery bank in 1 year (annual throughput)
R batt,f : Maximum life regardless of throughput (float life of the battery)
C rep,batt : Replacement cost of the battery bank
η rt : Round-trip efficiency
C ann,tot : Total annualised cost
i: discount rate
R proj : Project Lifetime
CRF(i, R proj ): Capital Recovery Factor
In university premises, electric power supply is available almost all the time and the problem of power outage only occurs in case of severe fault conditions which happens very rarely. The average feed in tariff or grid sell back price of 7 INR/unit is assumed for analysis generated through solar PV and wind turbine system [19, 20].
Analysis of various microgrid topologies based on the considered load profile are as follow:
6.1 Case I: Diesel Generator (168 kW)
In this case, it is assumed that there is no power supply form conventional grid as well as from renewable energy resources. Diesel generator is only the single power source for meeting the whole load demand. This is the worst case in terms of cost of electricity (COE), Net Present Cost (NPC), Operating Cost (OC) and CO2 emissions having high values of INR 35.48 INR 166 M, INR 12.5 M and 544705 kg/year. respectively. So, supplying power to meet demand only from diesel generator is not a desirable case in terms of economical and environmental aspect.
6.2 Case II: Utility Grid
In this case, it is assumed that all the load demand is supplied by utility Grid. Here, it is assumed that there is no single outage and Grid is available to supply power all over the time. The COE, NPC, OC and CO2 emissions obtained in this case are INR 6.0, INR 28.1 M, INR 2.17 M and 228933 kg/year. respectively.
6.3 Case III: Diesel Generator (110 kW), PV (150 kW), wind turbine (100 kW) and Battery bank (250 kWh)
In this case, it is assumed that there is no Grid supply and load demand is fulfilled by the combination of diesel generator and renewable energy sources i.e. through solar PV and wind turbine system. The COE, NPC, OC and CO2 emissions obtained in this case are INR 18.65, INR 87.3 M, 5.36 M and 231948 kg/year. respectively.
6.4 Case IV: Grid and Wind Turbine (100 kW)
In this case, only Grid and wind turbine system are responsible for meeting load demand. The COE, NPC, OC and CO2 emissions obtained in this case are INR 4.64, INR 25.7 M, 1.52 M and 146436 kg/year respectively.
6.5 Case V: Grid, PV (150 kW) and Battery bank (250 kWh)
In this case, only Grid and solar PV system are responsible for meeting load demand. The COE, NPC, OC and CO2 emissions obtained in this case are INR 2.95, INR 18.6 M, 0.896998 M and 106497 kg/year. respectively. If a battery bank of 250 kWh is added in this case to store excess electricity and for supplying power to load in emergency conditions then the value of COE, NPC, OC and CO2 emissions will change and increases to INR 3.83, INR 23.2 M, INR 1.11 M and 118289 kg/year. respectively.
6.6 Case VI: Grid, PV (150 kW), Wind Turbine (100 kW) and Battery bank (250 kWh)
From the analysis of various cases as discussed above, it is clear that a combination of grid, solar PV and wind turbine system seems to be the most desirable one in term of economical as well as environmental aspect, because all the values obtained here are the most favourable as compared to other cases.
Demand of electricity is increasing day by day and fossil fuels are limited for power generation, so there is a need to adopt non-conventional and environmental friendly methods of power generation to meet the country’s requirements. In view of this Government of India also initiated several subsidy schemes and missions like Jawaharlal Nehru National Solar Mission etc. for setting up power generation project using renewable energy resources. Deployment of microgrids is one of the best available technology for achieving this goal. Educational institutes have a responsibility to become a role model for the nation to save energy and promote optimization. These institutes support many students, research scholars, faculties and training facilities which can be a good platform to raise the awareness and promote energy saving. In view of this, different microgrid topologies are considered and analyzed in this paper. For different locations and system constraints, these microgrid topologies may differ. Many software’s are available to analyze technical and economical feasibilities. HOMER optimization tool is used in this paper to check all the possible combinations and configurations. Based on large number of simulation results obtained from HOMER, a combination of grid, solar PV and wind turbine system is found to be the most optimal case for the specified load. In this case, the value of COE, NPC, OC and CO2 are found to be less with respect to the other considered topologies.
Availability of data and materials
All data is given in the paper or properly cited wherever necessary.
FI carried out all the simulation work along with drafting of the manuscript under the guidance of ASS. Both authors read and approved the final manuscript.
1Fahad Iqbal is currently pursuing Ph.D from Department of Electrical Engineering, Jamia Millia Islamia (Central University), New Delhi-110025, India. He received M.Tech degree with Honors in Electrical Power System Management from Department of Electrical Engineering, Jamia Millia Islamia New Delhi, India. He was awarded Gold Medal for his outstanding performance in Master’s Degree. He received B.Tech. degree with Honors in Electrical and Electronics engineering from Integral University, Lucknow, India. He was awarded Silver Medal for his outstanding performance in Bachelor’s degree. His areas of interest are Microgrids, DG’s, DER’s, Renewable Energy Resources, FACTS devices, Power system Management and Power System Deregulation.
2Anwar Shahzad Siddiqui obtained his B.Sc. Engg. (Electrical Engineering) and M.Sc. Engg. (Power Systems and Electrical Drives) degrees from AMU, Aligarh, both with Honors in 1992 and 1994 respectively. He earned his Ph.D. degree from Jamia Millia Islamia (Central University) New Delhi, India in 2001. He has been teaching and guiding research in Electrical Engineering for about one and a half decade at AMU, Aligarh; JMI, New Delhi and BITS Pilani—Dubai Campus. His research interests include Power System Management and Applications of Artificial Intelligence Techniques in power System. He has more than 80 research papers published in refereed international and national journals and conference of repute.
The authors declare that they have no competing interests.
Consent for publication
Ethics approval and consent to participate
Open AccessThis article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.
- Iqbal, F., Khan, M.T., & Siddiqui, A.S. (2017). Optimal placement of DG and DSTATCOM for loss reduction and voltage profile improvement. Alexandria Engineering Journal. http://www.sciencedirect.com/science/article/pii/S1110016817300923. Accessed 20 June 2017.
- Dey, A. N., & Basak, P. (2015). A report on relevance of microgrid for developing countries with specific reference to India. International Journal of Advanced Research in Electrical, Electronics and Instrumentation Engineering, 4(6), 5484–5489.Google Scholar
- Nehrir, M. H., Wang, C., Strunz, K., Aki, H., Ramakumar, R., Bing, J., Miao, Z., & Salameh, Z. (2011). A review of hybrid renewable/alternative energy systems for electric power generation: configurations, control, and applications. IEEE Transactions on Sustainable Energy, 2(4), 392–403.View ArticleGoogle Scholar
- Kirthiga, M. V., Daniel, S. A., & Gurunathan, S. (2013). A methodology for transforming an existing distribution network into a sustainable autonomous micro-grid. IEEE Transactions on Sustainable Energy, 4(1), 31–41.View ArticleGoogle Scholar
- Wang, D., Ge, S., Jia, H., Wang, C., Zhou, Y., Lu, N., & Kong, X. (2014). A demand response and battery storage coordination algorithm for providing microgrid tie-line smoothing services. IEEE Transactions on Sustainable Energy, 5(2), 476–486.View ArticleGoogle Scholar
- Aghatehrani, R., & Kavasseri, R. (2013). Sensitivity-analysis-based sliding mode control for voltage regulation in microgrids. IEEE Transactions on Sustainable Energy, 4(1), 50–57.View ArticleGoogle Scholar
- Securicon Information Security Solutions. (2013). Introduction to Microgrids. http://securicon.com/content/new-white-paper-introduction-microgrids-2. Accessed 12 Jan 2016.
- Banerji, A., Sen, D., Bera, A. K., Ray, D., Paul, D., Bhakat, A., & Biswas, S. K. (2013). Microgrid: A review (pp. 27–35). Trivandrum: IEEE Global Humanitarian Technology Conference: South Asia Satellite (GHTC-SAS).Google Scholar
- Ahmad, F., & Iqbal, S. (2012). Reducing Electricity Consumption in Educational Institutes: A Case Study on Aligarh Muslim University’s Electricity Usage Scenario. IEEE Students’ Conference on Electrical, Electronics and Computer Science, MANIT Bhopal, 2012, 34-38. Google Scholar
- Annual Report 2014-2015, Aligarh Muslim University. http://www.amu.ac.in/annreport.jsp. Accessed 05 Jan 2016.
- Archives 2015, Electricity Department, AMU, India. http://www.amu.ac.in/electricity.jsp?did=10075. Accessed 03 Jan 2016Google Scholar
- Proceedings of Workshop on Energy Efficiency and Audit for AMU, BEE India. https://www.beeindia.gov.in/content/energy-auditors. Accessed 21 June 2014.
- Ali, I., & Hussain, S. M. S. (2016). Communication design for energy management automation in microgrid. IEEE Transactions on Smart Grid, 99, 1–1. doi:10.1109/TSG.2016.2606131.View ArticleGoogle Scholar
- Hafez, O., & Bhattacharya, K. (2012). Optimal planning and design of a renewable energy based supply system for microgrids. Renewable Energy, 45, 7–15.View ArticleGoogle Scholar
- Lambert, T., Gilman, P., & Lilienthal, P. (2005) Micropower System Modelling with HOMER. In Integration of Alternative Sources of Energy, pp. 379 – 415. John Wiley & Sons, Inc., Hoboken, NJ, USA. doi: 10.1002/0471755621.ch15.Google Scholar
- NASA Surface meteorology and Solar Energy: HOMER Data. https://eosweb.larc.nasa.gov/cgi-bin/sse/HOMER.cgi. Accessed 08 Jan 2016.
- Li, Y., Chen, X., Xiao, J., & Wei, X. (2014). Optimal configuration for distributed generations in micro-grid system considering diesel as the main control source. IEEE Proceedings of the 2014 International Conference on Advanced Mechatronic Systems (ICAMechS), Kumamoto, 2014, 552-556.Google Scholar
- Synergy enviro engineers. http://www.synergyenviron.com/. Accessed 20 June 2017.
- Press Information Bureau, Government of India, Ministry of New and Renewable Energy. http://pib.nic.in/newsite/PrintRelease.aspx?relid=133220. Accessed 10 Jan 2016.
- Why sun is shining on solar power. The Tribune, Voice of the people. Sunday Special, Kaleidoscope. http://www.tribuneindia.com/news/sunday-special/kaleidoscope/why-sun-is-shining-on-solar-power/72297.html. Accessed 18 Jan 2016.