- Original research
- Open Access

# Research on fault diagnosis for MMC-HVDC Systems

- Zhiqing Yao
^{1}Email author, - Qun Zhang
^{2}, - Peng Chen
^{2}and - Qian Zhao
^{2}

**1**:8

https://doi.org/10.1186/s41601-016-0022-0

Β© The Author(s) 2016

**Received:**13 May 2016**Accepted:**16 May 2016**Published:**30 June 2016

## Abstract

### Introduction

With the development of flexible HVDC technology, the fault diagnosis of MMC-HVDC becomes a new research direction.

Based on the fault diagnosis theory, this paper proposes a robust fault diagnosis method to study the fault diagnosis problem of MMC-HVDC systems.

### Methods

By optimizing the gain matrix in the fault observer, fault detection with good sensitivity and robustness to disturbance is achieved. In the MMC-HVDC system, because of the inherently uncertain system and the presence of various random disturbances, the study of robust fault diagnosis method is particularly important.

### Results

Simulation studies during various AC faults have been carried out based on a 61-level MMC-HVDC mathematical model. The results validate the feasibility and effectiveness of the proposed fault diagnosis method.

### Conclusions

So this fault diagnosis method can be further applied to the actual project, to quickly achieve system fault diagnosis and accurately complete fault identification.

## Keywords

- Fault diagnosis
- MMC-HVDC
- Robust
- State observer
- Residual state equation

## Introduction

In recent years, due to the increased size and complexity of control systems, fault diagnosis becomes particularly important, especially in power systems [1]. For instance, if line faults are not quickly detected and isolated, they can cause system failure or even lead to disastrous consequences [2]. Currently, there are many fault diagnosis methods, such as the diagnostic filter method, parameter identification method, expert system, artificial neural network etc. [3β5]. Although these methods can effectively detect failures in the system, they cannot precisely estimate these fault signals.

This paper proposes a fault diagnosis method based on full dimension state observer for flexible HVDC system. State estimation is carried out using the mathematical model of a three-phase 61-level modular multilevel converter (MMC) based HVDC (MMC-HVDC) system and the full dimension state observer. Residual state equation is established and is combined with the system output and system phasor. By optimizing the gain matrix in fault observer, the robustness of the fault detection is investigated. In the MMC-HVDC system, because the system is inherently uncertain and there are various random disturbances, the study of robust fault diagnosis method is particularly important.

## Methods

### Model of MMC-HVDC

_{.}

**Ξ**(

*t*) represents uncertainty and external disturbances generated during the actual modeling process.

**f**(

*t*) represents the system faults which are required to detect and identify.

**M**(

*t*) is measurement noise introduced by the measurement system.

**B**

_{ f },

**C**and

**D**are known matrices with appropriate dimensions.

**y**(

*t*) is the system output. If

**Ξ©**(

*t*) is used to represent

**Ξ**(

*t*)β+β

**h**(

*t*), Eq. (7) can be written as follows.

- 1)
Uncertainties in the system are norm-bounded, that is β

**Ξ**(*t*)βββ€β*V*_{Ξ}. - 2)
System matrix pair (

**A**,**C**) is observable. - 3)
Uncertainties in the system meet the condition β

**Ξ©**(*t*)βββ€β*Ξ³*β**x**(*t*)βββ€β**V**_{Ξ©}. - 4)
The

**M**(*t*) in the system is norm-bounded, that is β**M**(*t*)βββ€β*V*_{ M }. - 5)
The initial state of the system is zero.

### Design of full dimension state observer

Fault diagnosis is carried out by full dimension state observer based on the state equation of flexible HVDC system [12β14]. It can be seen from Eq. (8) that **Ξ©**(*t*) contains the system uncertainties and external disturbance, and the grid voltage u_{a}, u_{b}, u_{c}, which can be regarded as unknown nonlinear perturbation term.

**r**(

*t*)β=β

**y**(

*t*)βββ

**Ε·**(

*t*), Eq. (10) can be written as follows:

**r**(

*t*) is presented by

**T**

_{ rd }whereas

**T**

_{ rf }presents the transfer function from system fault to residual

**r**(

*t*). If the value of β

**T**

_{ rd }β is small enough and the value of β

**T**

_{ rf }β is big enough in the design, the designed observer will be robust. Therefore, the following performance index is used to design the fault diagnosis observer:

Equation (13) can be solved by using multi-objective optimization methods and thus the robust control theory will be used to solve the performance optimization problem proposed by Eq. (13).

### Theorem 1

**D**

^{ T }

**D**βββ

*Ξ²*

^{2}

**I**β<β0. In case of no fault in the system, if there are a positive definite symmetric matrix R and a constant factor

*Ξ΅*

_{1}β>β0 meeting the following linear matrix inequality:

*r*(

*t*)β

_{β}ββ€β

*Ξ²*β

*d*(

*t*)β

_{β}.

### Theorem 2

*Ξ·*is given and satisfies the condition

**D**

^{ T }

**D**βββ

*Ξ·*

^{2}

**I**β<β0. In case of no fault in the system, if there are a positive definite symmetric matrix T and a constant factor

*Ξ·*

_{1}β>β0 meeting the following linear matrix inequality:

The residual system (11) is asymptotically stable and meets β*r*(*t*)β_{β}ββ₯β*Ξ·*β*f*(*t*)β_{β}.

### Theorem 3

*Ξ²*β>β0,

*Ξ·*β>β0 are given. If there are positive definite symmetric matrix R, T,H, constant factor

*Ξ΅*

_{1}β<β0 and

*Ξ·*

_{1}β>β0 meeting the following linear matrix inequality:

The residual system (11) is asymptotically stable and meets β*r*(*t*)β_{β}ββ€β*Ξ²*β*d*(*t*)β_{β} and β*r*(*t*)β_{β}ββ₯β*Ξ·*β*f*(*t*)β_{β}.

The gain matrix H of the full dimension state observer can be obtained from Theorem 3. The design process of gain matrix H takes into account the impact of system disturbances and uncertainties on the residual, and the sensitivity of the residual for faults.

### Determination of fault detection threshold

When disturbances or uncertainties exist in the system, a fault detection threshold method is usually used to determine whether the system has a fault [15β17]. This section provides fault detection thresholds calculated according to the definition of norm.

### Theorem 4

The system represented by Eq. (8) satisfies the assumptions (1)-(5). If the residual system (11) meets β**r**(*t*)ββ>β(*a*
**V**
_{Ξ©}β+β*b*
**V**
_{
M
})(*t*βββ*t*
_{0})β+β*c*
**V**
_{
M
}, then system fault is detected,where \( a=\underset{t\in \left[{t}_0,t\right]}{ \sup}\left\Vert \mathbf{C}\boldsymbol{\Psi } \left(t,s\right)\right\Vert \), \( b=\underset{t\in \left[{t}_0,t\right]}{ \sup}\left\Vert \mathbf{C}\boldsymbol{\Psi } \left(t,s\right)\mathbf{H}\mathbf{D}\right\Vert \), \( c=\underset{t\in \left[{t}_0,t\right]}{ \sup}\left\Vert \mathbf{D}\right\Vert \).

### Proof

**e**(

*t*

_{0})β=β0. Thus

Proof is done.

## Results

### Simulation results

According to the MMC-HVDC system state Eq. (7), common types of fault, e.g. phase A to ground fault, phase-AB to ground fault, three phase to ground fault are simulated based on the 61-level MMC-HVDC system using Matlab/Simulink and RT-LAB.

### Phase-A to ground fault

Figure 2 shows the DC bus voltage and current waveform when the phase-A to ground fault occurs in the rectifier side. The fault is introduced at 0.5 s when the system is running at steady state. The residual characteristics of the DC bus voltage and current can be calculated by the MMC-HVDC system residual state Eq. (13), as shown in Fig. 3. The baseline reference points of the HVDC fault observer output voltage and current are zero, which can be seen by comparing Figs. 2 and 3. When the system operates normally, taking into account the existing uncertainties and various random disturbances, residual curve should fluctuate within a limited range. From Fig. 3 it can be seen that, after a system fault, the system output curves (the DC bus voltage and current) significantly deviate from zero and their normal bands. The systemβs fault diagnostic threshold can be calculated according to Theorem 4. If the residual waveform fluctuates within the calculated threshold, it is judged that the system is operating normally. If the residual waveform exceeds the calculated threshold, a fault is detected and immediate protection action should be taken. Furthermore, the fault identification and fault estimation can also be studied according to the residual waveform. As seen from the simulation, when tβ>β0.52 s, it detects a fault in the system.

### Phase-AB to ground fault

The waveforms during phase-AB to ground fault are shown in Fig. 4 where the fault is introduced at 0.5 s. Due to the existence of various disturbances and uncertainties in the system, measurement noise is inevitably introduced when measuring system output. The residual voltage and residual current waveforms are shown in Fig. 5. According to Theorem 4, the fault detection threshold is Jthβ=β0.136 * 104. As seen from the simulation, when tβ>β0.52 s, the fault is detected.

### Three phase to ground fault

The waveforms during three phase to ground fault is shown in Fig. 6. The fault is again introduced at 0.5 s. The residual voltage and residual current waveforms calculated according to residual system state equation are shown in Fig. 7. According to Theorem 4, the fault detection threshold is Jthβ=β2.62*104. As seen from the simulation, when tβ>β0.52 s, the system fault is detected.

## Conclusions

In this paper, a robust fault diagnosis method is proposed to detect system fault in MMC-HVDC power transmission systems. The advantage of the proposed method is that the state observer considers the system uncertainties and fault sensitivity. Therefore, the proposed method can quickly achieve system fault diagnosis and accurately complete fault identification. The simulation results have proved the effect of robust fault diagnosis.

## Declarations

### Authorsβ contributions

ZQY analyzed and proposed the robust fault diagnosis method. QZ, PC and QZ completed the simulations on RT-LAB and the written of this paper. ALL the authors read and approved the final manuscript.

### Competing interests

The authors declare that they have no competing interests.

**Open Access**This article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.

## Authorsβ Affiliations

## References

- Zhang, ST, & Hao, JJ. (2012). Fault diagnosis based on multiple-models particle filter.
*Control Engineering of China, 19*(5), 864β871.Google Scholar - Song, ZM, Guo, YH, Xun, TS, et al. (2012). Reaserch on HVDC transmission system fault analysis based on wavelet transform.
*Power System Protection and Control, 40*(3), 100β104.Google Scholar - Bian, L, & Bian, CY. (2014). Review on intelligence fault diagnosis in power networks.
*Power System Protection and Control, 42*(3), 146β158.Google Scholar - Li, HW, Yang, DS, Sun, YL, et al. (2013). Study review and prospect of intelligent fault diagnosis technique.
*Computer Engineering and Design, 34*(2), 632β637.Google Scholar - Wang, JL, Xia, L, Wu, ZG, et al. (2010). State of arts of fault diagnosis of power systems.
*Power System Protection and Control, 38*(18), 210β216.Google Scholar - Dai, GF, Zhao, D, Lin, PF, et al. (2015). Study of control strategy for active power filter based on modular multilevel converter.
*Power System Protection and Control, 43*(8), 74β80.MathSciNetGoogle Scholar - Gnanarathna, UN, Gole, AM, & Jayasinghe, RP. (2011). Efficient modeling of modular multilevel HVDC converters (MMC) on electromagnetic transient simulation programs.
*IEEE Transactions on Power Delivery, 26*(1), 316β324.View ArticleGoogle Scholar - Peralta, J, Saad, H, Dennetiere, S, et al. (2012). Detailed and averaged models for a 401-level MMC-HVDC system.
*IEEE Transactions on Power Delivery, 27*(3), 1501β1508.View ArticleGoogle Scholar - Simon, P.T. Simplified dynamic model of a voltage sourced converter with modular multilevel converter design. IEEE/PES Power Systems Conference and Exposition. Seattle, USA, 2009: 1β6Google Scholar
- Simon, P.T. Modeling the trans bay cable project as voltage-sourced converter with modular multilevel converter design. IEEE Power and Energy Society General Meeting. Michigan, USA, 2011: 1β8Google Scholar
- Guan, M, & Xu, Z. (2012). Modeling and control of modular multilevel converter based HVDC system under unbalanced grid conditions.
*IEEE Transactions on Power Electronics, 27*(12), 4858β4867.View ArticleGoogle Scholar - Zhu, QL, Peng, CH, Li, JF, et al. (2012). Fuzzy DTC of PMSM based on full order observer.
*Power Electronics, 46*(1), 87β89.Google Scholar - Yang, JQ, & Zhu, FL. (2014). Linear-matrix-inequality observer design of nonlinear systems with unknown input and measurement noise reconstruction.
*Control Theroy & Applications, 31*(4), 538β544.Google Scholar - Gao, H, & Cai, XS. (2013). Functional obsever design for a class of nonlinear systems.
*Control Theory & Applications, 30*(9), 1207β1210.Google Scholar - Zhao, Y, Dong, S, & Li, TY. (2010). A new adaptive threshold algorithm to partial discharge processing based on HHT-MDL criterion.
*Power System Protection and Control, 38*(5), 45β50.Google Scholar - Zhu, XH, Li, YH, Li, N, et al. (2013). Novel observer-based on robust fault detection method for nonlinear uncertain systems.
*Control Theory & Applications, 30*(5), 644β648.Google Scholar - Qin, LG, He, X, & Zhou, DH. (2015). A fault estimation method based on robust residual generators.
*Journal of Shanghai Jiaotong University, 49*(6), 768β744.Google Scholar